for New Albany, OH
Scheduled maintenance cooling tune up on a Bryant air conditioner completed. I visually inspected the furnace. Checked voltage and amps. I inspected the evaporator coil. I checked the temperature difference across the coil. Checked refrigerant charge, voltages and amps. I rinsed the condenser coils with water. Cycled and monitored the system. Operating normally at this time.
I provided an estimate on a Carrier 13 SEER 4 Ton Air Conditioner. I will wait to hear from the customer on how they want to move forward.
Upon inspection, I informed the customer that getting mini splits in the master bedroom could be his best option since the furnace is working, but not reaching the bedroom. I informed the customer I would have to come back out with my manager to fully go over mini split options. System is operational upon departure.