for Sunbury, OH
Trane A/C System found to have a blown capacitor. With customer approval, replaced the Dual Capacitor and cycled the system on and is now cooling properly.
Final inspection performed on new install of a Carrier Gas Furnace and Air Conditioner. Tune-Up and Safety Checkout also performed on Carrier Gas Furnace. System is ready for the upcoming cooler season.
Installed a Carrier 80% 90,000 BTU Gas Furnace and Carrier 13 SEER 2.5 Ton Air Conditioner.
Further inspection of a Carrier 13 SEER 2 Ton Air Conditioner and found Nest thermostat malfunctioning. Installed a Honeywell Lyric WiFi thermostat and system is properly cooling now.
Comfortmaker air conditioner repair
Installation of a Carrier 96% Multi-Speed 100,000 BTU Gas Furnace